1. Laminar flow operating room cleaning equipment routine inspection 1, equipment operation management level. The laminar flow operating room needs full-time operation and management personnel of purifying equipment, clear and
1. Laminar flow operating room cleaning equipment routine inspection 1, equipment operation management level. The laminar flow operating room needs full-time operation and management personnel of purifying equipment, clear and enforceable management system, correct and reasonable operation plan, safety guarantee and emergency response ability, and effective safeguard measures, equipment running sound, no odor, internal cleaning, no water no dust, clean room, good ventilation. 2. Internal Inspection of the unit. The blower works normally, the belt is loose and tight, the bearing is not abnormal hot; the cold and Hot coil pipe is normal, the fin is clean without lodging block; the filter does not leak, does not block; Fresh air, exhaust, mixed air valve flexible action, Fresh Air Valve Exhaust Valve synchronization is good; steam pressure is normal, the actuator does not leak;. 3. Performance. Laminar flow operating room temperature and humidity control accuracy, temperature and humidity fluctuations, to meet the requirements. Lack of wind alarm, high temperature alarm, disinfection lamp alarm, refrigeration unit alarm, fan failure alarm, filter differential pressure alarm and other normal work. Second, Laminar flow operating room cleaning equipment regular maintenance content, weekly maintenance: Clean Laminar flow operating room hygiene, ensure laminar flow operating room clean without debris, no dust, air smooth; Check the valve, pressure gauge, pressure relief valve, humidifier valve is sensitive and reliable; check whether the disinfection UV lamp is working properly, test whether the UV irradiation intensity is qualified; Is the sound of each part normal when the laminar flow operating room cleaning equipment is running. Keep weekly maintenance records. MONTHLY MAINTENANCE: Laminar flow operating room cleaning equipment internal cleaning, check the machine box equipment is abnormal; cleaning condensate dish; humidifier check cleaning; blower belt adjustment; check air flow, clean operating room air pressure test. Quarterly maintenance: Check the light and switch; check the sealing performance of the cabinet door; check the steam trap valve (frozen water filter, hot water filter) ; replace the medium efficiency filter; check whether the fan, motor rotation is flexible, there is no abnormal sound; Check the fan shock absorber spring is normal; check the loose phenomenon of the components. Annual maintenance: check, clean the Muffler; check the heater and refrigeration equipment; check the ventilation pipe and related equipment; check the air hose connection aging damage; check whether the humidification equipment work reliably; Clean the inside and outside of the unit. Annual summary: Weekly, monthly, quarterly, annual maintenance content, replacement parts name, specifications, quantity, maintenance level, equipment operation status to make a summary. It is suggested that the Laminar flow operating room cleaning equipment is defective in operation, and the parts need to be repaired and replaced. To evaluate the safety operation of Laminar flow operating room cleaning equipment.